AEIC CS Specifications for Thermoplastic and Crosslinked Polyethylene Insulated Shielded Power Cables Rated 5 through 35 kV, 9th Edition, AEIC CS, Specification for Impregnated Paper and Laminated Paper AEIC CS, Specifications for Cross-linked Polyethylene. AEIC CS, Specifications for Crosslinked Polyethylene Insulated . aFor use with % insulation level cable as defined in AEIC CS or AEIC CS
If you’re shopping for medium-voltage cable, some very familiar requirements are about to change – and you’ll need to learn some new numbers. These specifications describe a 3 conductor, neutral supported, service drop cable rated at volts and consisting of two insulated aluminum conductors twisted around a bare neutral aaeic further specified below. Size and type of cable d.
Neutral conductor shall be Bare stranded ACSR aluminum, and of equivalent size of the insulated conductors. You have to check your accessories to see if they will accept the smaller diameters.
Ware concludes, “Overall, we feel it’s in the best interest of the utility industry to move to the new standards. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Transformed into ANSI Standards
Phase conductor shall be stranded aluminum with cross-Linked Polyethelene Insulation. A waterproof tag shall be firmly affixed to each reel having the following information: New Numbers To Know Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards If you’re shopping for medium-voltage cable, some very familiar requirements are about to change – and you’ll need to learn some new numbers.
Diameter of shield in. City of Ocala, Central purchasing. Cable spec clarification letter. All ingredients shall be mixed through an appropriate screen pack and then. Reference must be made to City of Ocala purchase order number, quantity, and weight of.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards.
Joint task force drafted new standards. Triplexed volt secondary underground distribution cable; “EC” grade aluminum hard drawn conductor in accordance with ASTM B; Class B standing in accordance with ASTM B; Insulation shall be cross-linked polyethylene with minimum average thickness of 78 mils.
If the rise times of the pseudoglow discharges are too longthey aeuc evade detection by pulse detectors as covered in Test Method D Reel Qeic, tare, and net weight. We’re encouraging our customers to include them in the purchasing process.
Historical Version s – view previous versions of standard. Quadruplex volt secondary underground distribution cable; “EC” grade aluminum hard drawn conductor in accordance with ASTM B; Class B standing in accordance with ASTM B; Insulation shall be cross-linked polyethylene with minimum average thickness of 78 mils.
Transformed into ANSI Standards
Also in some applications, like turbogenerators, where a low molecular weight gas such as hydrogen is used as a coolant, it is possible that pseudoglow discharges will develop. In most of the applications, it’s not a problem. These tests shall include the electrical and thermomechanical.
YES designates that the cable shall be marked with sequential footage markers for the entire length of the cable. Therefore, foreign-based manufacturers will need to supply documentation that clearly shows that the cable is made in the USA.
The City of Ocala is looking to purchase the following items: ANSI acceptance adds authority. Size and type of cable.
Length of cable e. Specific precaution statements are given in Section 7. Bidders can be approved by contacting Mary Ann St.
Material Manual Stock Number Maximum reel diameter to be 66″. It is possible that such partially conducting surfaces ds5 develop with polymers that are exposed to partial discharges for sufficiently long periods to accumulate acidic degradation products. Link to Active This link will always route to the current Active version of the standard.
The utility industry’s long-standing requirements for cross-linked polyethylene Afic and ethylene propylene rubber EPR MV cable insulations have been combined into a single document that has been accepted by the American National Standards Institute.
Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards Specifying Cable? Association of Edison Illuminating. In the new MV standards scheme, the requirements are very similar, but they’re organized by cable architecture.